manual, RUN/STOP, and alarms) and the PV or SV. E5CN/E5AN/E5EN/E5GN Digital Temperature Controllers User’s Manual Basic Type E5CN-R2MT E5CN/E5AN/E5EN Digital Temperature Controllers User’s Manual Basic E5CN -R2MT AC or E5CN-R2MTD AC/DC24). E5CN/E5CN-U Temperature Controller User’s Manual (Cat. No. H). E5CN Temperature Controller Communications User’s Manual (Cat. E5CN-R2MT-
|Published (Last):||15 December 2009|
|PDF File Size:||16.25 Mb|
|ePub File Size:||5.92 Mb|
|Price:||Free* [*Free Regsitration Required]|
OMRON E5CN Datasheet: Ordering Information
Back-connecting Socket P3GA 27 dia. An SELV circuit is one separated from the power supply with double insulation or reinforced insulation, that does not exceed 30 V r.
Can also be mounted to a DIN track. Easily see the status from a distance with PV display with threecolor switching function. SSR failure detection alarm setting range 0. Set the alarm types for alarms 1 to 3 independently in the initial setting level.
Ordering Information – Omron E5CN Datasheet [Page 3]
Panel cutout, Internal panel dimensions for panel mounting, wiring screw sizes, wiring terminal arrangement, and parameter setting methods.
When placing the Controller back in the case, make sure that electronic parts do not come in contact with the case.
In no event e5ch-r2mt-500 the responsibility of OMRON for any act exceed the individual price of the product on which liability is asserted. If the control output terminals are connected to ground, errors will occur in the e5cnr-2mt-500 temperature values as a result of leakage current.
Do not use the Temperature Controller in the following locations. Setting protection indicator informs operator when protection is enabled. Transfer output provided for easy output to recorders. Starting in automatic mode Press the Level Key less than 1 s. Failure to do so may result in unexpected operation occasionally resulting in damage to equipment or personal injury.
When extending or connecting the thermocouple lead wire, be sure to use compensating wires that match manuall thermocouple types. Do not attempt to disassemble, modify, or repair the Temperature Controller or touch any internal components.
E5CN-Y Added models with long-life relay outputs. If an input error output is enabled, the al-1 operation indication on the front panel will not light and s. Option Unit can be mounted 4. Operation level entered for e5cn-r2mr-500 reset.
Loss of operation control or alarm outputs due to malfunction may occasionally result in physical damage to the controlled system or equipment.
Sections without any specification on their degree of protection or those with IP 0 are not waterproof. SP used by multi-SP Protect Level The time taken to move to the protect level can be adjusted by changing the “Move to protect level time” setting. Therefore, the service life can be extended by lowering the temperature of the Temperature Controller.
Set up the power supply so that the voltage will reach the rated voltage within 2 seconds after turning ON.
Tighten the terminal screws using a torque between 0. If you remove the Controller from its case, do not touch or apply shock to the electronic parts inside.
3 X c Manual Reset Thermostat Normal Closed Temperature Switch v 10a | eBay
Fire may occasionally occur if terminal screws become loose. Always consider the actual application conditions and be sure to use the output relay within its rated load and electrical life expectancy. Plug Two, M3 depth: These devices can cause radio disturbances which adversely affect the performance of the Controller. Do not connect anything to unused terminals. Protect Level Press the Level Manusl for at least 1 s.
EUROTHERM ERO LFS Controller PID Heater Break Alarm Rs485 W/ Manual Hardware
This enables the new E5CN to handle application requiring even greater response speed and accuracy. Connect to either a thermocouple or platinum resistance thermometer with the same model. Standard insulation is applied between any of the following: Tighten the two fixing screws on the adapter. Take appropriate safety measures, such as installing a separate monitoring system, to maunal safe operation in the event of a malfunction of the Temperature Controller.