Australian/New Zealand Standard™. Electrical installations—Shows and carnivals. A. S. /NZS This is a free 7 page sample. Access the full version online. AS/NZS Electrical installations – Shows and carnivals. standard by Australian/New Zealand Standards, 01/01/ View all product details. Find the most up-to-date version of AS/NZS at Engineering
|Published (Last):||2 May 2007|
|PDF File Size:||16.46 Mb|
|ePub File Size:||8.99 Mb|
|Price:||Free* [*Free Regsitration Required]|
For outdoor venues, there must be at least 2 alternative power supplies. For outdoor events, large signs illuminated by two light 3002, and large enough to make the exit location obvious to patrons must be used. Lighting should be energised approximately 1 hour before sunset to allow time for any unserviceable lights to be repaired before sunset. Home Electrical and lighting requirements — public buildings.
Electricity Safety Regulations Ministry: Luminaires Luminaires must be out of reach of the public and not located where heat may ignite adjacent materials. Sets out requirements for the supply of electricity at low-voltage by wiring systems to power consuming devices used for accommodation, entertainment or display purposes within – a concessions; b tents; c living quarters; and d other structures associated with events with a maximum duration of four weeks.
Two generators or a supply authority supply, plus another generator, are acceptable alternatives provided that the venue lighting supplies are distributed between both. Area lighting Temporary areas available to the public at night, nzzs concert areas, should always be illuminated.
Luminaires must be out of reach of the public and not located where heat may ignite adjacent materials.
AS/NZS – Quick Download AWS, SIA, BS EN, ISO Codes
Safety lighting must be a separate supply to normal or emergency lighting and must not be dimmed or modulated. All town supplies are connected this way but generators may not be. Expand the box to see details.
All electrical outlets and supplies must have circuit breakers to protect against overload. The Health Public Buildings Regulations external site nss electrical contractors to certify electrical installations including reticulated supplies by completing a Form 5. All referenced documents are displayed below. All electrical outlets must be protected by a RCD also known as a safety switch.
Bare lamps must not be able to be touched by the public. Small individual generators 10 kva or less should not be utilised. Each generator must be connected to its own earth electrode driven into the ground. Residual current devices — RCDs The preferred leakage tripping current is 30 milliamps and they must be tested every 12 months in accordance with the requirements of AS For the purposes of this Standard, events include exhibitions, shows, carnivals, scouting jamborees, army camps and the like.
It is recommended that for typical installations:. It is recommended that for typical installations: Leads must not be placed on the ground in areas where there is pedestrian traffic.
For crowded areas, especially for concerts and areas licensed to consume alcohol, there must be a system in place that will allow areas to flood light instantaneously in the event of an emergency. A copy of the Form 5: Standard multicore cables used in static installations are not appropriate. Where electrical outlets are provided, there should be a tie bar to allow electrical cords to be secured, to prevent tension on the electrical outlet.
All permanent venues and egress paths must be able to be illuminated to 40 lux by lighting that is:. Electrical leads and portable outlet devices All electrical outlets must be protected by a RCD also known as a safety switch. New equipment requires a tag to define when it was brought into service.
Dimensional interchangeability requirements for pin and contact-tube accessories AS Amusement rides and devices IEC Plugs socket-outlets and couplers for industrial purposes. International Classification nzz Standards ICS is an international classification system for technical standards. References This document may make references to other documents. Typical temporary installations consist of submains, subboards and electrical leads.
Maximum viewing distance Minimum pictorial element height mm 16 24 32 For viewing distances greater than 32 m, in accordance with the following equation: Other people who purchased this product also bought For RCDs to be effective, the neutral and earth conductors must be bonded together at the point of supply. It is recommended that this connection be made via a removable link.
It is designed to cover every economic sector and virtually every activity of the humankind where technical standards may be used.
See Testing of electrical leads and residual current devices RCDs Lighting All permanent venues and egress paths must be able to be illuminated to 40 lux by lighting that is: Supplies may originate from a supply authority or an on-site generator.
Safety lighting For events where lighting will be dimmed or extinguished, stairs, ramps and egress paths must be illuminated by safety lighting. Eelectrical contractors performing work in a public building must submit a Form 5 certificate of electrical compliance to the local government, to certify that permanent and temporary electrical installations are compliant with the unique requirements of the regulations and other ax obligations.
Because cables are continually being rolled up and moved, they must be flexible. Click Buy for Online Library subscription. This document may make references to other documents.
Submain cables must have integral earth and neutral conductors.